Use the filters below to limit the number of search hits.
Out of Range Alarms
When setting up an out of range alarm, you configure the normal range of the monitored variable. If the variable goes below the lower limit or above the upper limit of the normal range, the alarm is triggered.
Out of Reference Range Alarms
The out of reference range alarm monitors variable movements comparing to a reference variable. By setting an upper deviation limit and lower deviation limit, you configure the tolerance the monitored variable can vary from the reference variable before the alarm is triggered. The upper alarm limit of the monitored variable is equal to the reference point current value plus the upper deviation limit. The lower alarm limit of the monitored variable is equal to the reference point current value minus the lower deviation limit.
Properties and Watch Substitution Codes
Properties and Watch substitution codes represent the information you want to display when a notification report is triggered. The information is dynamically filled in from the properties or Watch data that are included in the notification report.
Reset Style Properties
Use the Reset Style properties to edit and view the colors and fonts of alarms in the Alarms pane and Alarm Views that are in Reset state.
Save Favorite Dialog Box
Use the Save Favorite dialog box to save a new Alarms pane, Events pane, Alarm View, or Event View favorite layout and filter conditions, or to overwrite an existing pane or View layout and filter conditions by saving it under an existing name.
Select Conditions Dialog Box
Use the Select Conditions dialog box to sort out the alarms of interest in the Alarms pane or an Alarm View, or the events in the Events pane or an Event View.
A shunt variable is a binary value that works as an on/off switch for the alarm.
When you select the acknowledgment type Single acknowledgment, the user needs to acknowledge the alarm in the alarm view before the alarm returns to normal state and disappears from the alarm view.